• Remove jumper. iii. Simulate Ignition or Flame Failure: • Follow procedure to turn on burner. • Close hand valve in oil supply line. • Failure occurs, device enters Recycle Mode. Indicator light flashes at . Hz rate 2 seconds on, 2 seconds off). • Device tries to restart system after approximately 60 seconds. • After third Recycle Mode trial, safety switch locks out within safety switch timing indicated on label and control enters Restricted Mode. Indicator light flashes at 1 Hz rate (. second
P. AqUASTAT CONTROLLER INSTALLATION (BOILERS WITH TANKLESS HEATER ONLY). 1. On boilers with tankless heater, install the L4006A aquastat controller well (found in Part Carton) into .” NPT tapping in tankless heater plate. 2. Remove the L4006A aquastat controller with factory attached harness from Control Carton. 3. Slip the bulb of the aquastat controller into the well and secure the controller in place with the set screw. WARNING Aquastat bulb must be fully inserted into the well. 4. Feed the L
5. For boiler located in a confined space or an unconfined space in a building of unusually tight construction, provide outdoor air. a. Outdoor air for combustion may be provided with an optional Burnham Inlet Air Accessory Kit, Part Number 611280031 (only available and suitable for use on Beckett AFG with burner enclosure cover burner). See Section V for installation details. or b. Outdoor air may be provided with the use of two permanent openings which communicate directly or by duct with the
MPO sections are produced in Burnham’s own state-of-the-art foundry in Zanesville, Ohio, and are the primary reason why the MPO is able to attain an ENERGY STAR-certified 87% AFUE. Built-in Return Water Boiler Protection Every MPO boiler comes equipped with a unique return water blending device that automatically mixes hot boiler water with cool return water. This device also aids in keeping temperatures consistent within the boiler which provides greater operational efficiencies and allow the b
FT. (4) (5) MAXIMUM AIR INLET LENGTH EQUIV. FT. (4) (5) AFUE% APPROX. SHIPPING WEIGHT (LBS.) MMII 4-70 70 58 50 2.9 70 70 83.3 307 MMII 4-105 105 84 73 3.1 70 70 80.2 307 MMII 5-105 105 88 77 3.1 70 70 83.3 345 MMII 5-140 140 112 97 3.3 70 70 80.1 345 1. If LP gas specify on order. Ratings are the same. 2. AGA Ratings shown are for installations at sea level and elevations up to 2,000 ft. For eleva tions above 2,000 ft. A.G.A. ratings should be reduced at the rate of four percent (4%) for
More make-up water and higher concentrations of contaminants damage the boiler sooner. Our warranty does not cover oxygen corrosion and sediment- related damage. Clearly it is in everyone’s best interest to prevent this type of failure. You can do your part by ensuring that your system is leak-free. D. ATTENTION TO BOILER wHILE NOT IN OPERATION. NOTICE If boiler is not used during winter time, it must be fully drained to prevent freeze damage. 1. Spray inside surfaces with light lubricating or c
The burner will operate in the following sequence: Prepurge for the first 10 seconds; fire until the thermostat is satisfied or the limit setting on the high limit is reached; post-purge for the last 10 seconds. When the pressure limit control restores the circuit on a drop in pressure, the burner will start if the thermo stat is still calling for heat. The probe low water cut-off will shut down the burner after a 10-15 second delay, if the water level in the boiler drops below the probe level.
Price - $3.00 ™maetSageMRELIOBLIOSSAP-3gnikeesnehW.reilppusliororotcartnocgnitaehruoyllac,reliobotsriaperroecivresroFgnitaRnonwohssarebmuNlaireSdnarebmuNledoMrelioBedivorp,reliobnonoitamrofni.reliobehtfopotnodetacollebaLrebmuNledoMrelioBrebmuNlaireSrelioBetaDnoitallatsnITSMrotcartnoCgnitaeHrebmuNenohPsserddA IMPORTANT INFORMATION - READ CAREFULLY The following terms are used throughout this manual to bring attention to the presence of hazards of various risk levels, or to important information c
7. Feed Molex end of Burner Harness thru front jacket panel right side outlet receptacle cutout. Insure that the receptacle middle prong opening is facing down. Snap the receptacle into front jacket panel. Temporarily, stuff Molex end of Burner Harness between front panel insulation and insulation wrapper near boiler top. J. SIDE AND TOP JACkET PANEL INSTALLATION. 1. Pick up Left Side Jacket Panel from Jacket Carton. See also “Repair Parts” Section, “Jacket Assembly” illustration for part identi
for both firing rates. 5. As an ENERGY STAR partner, Burnham has determined that this product meets the ENERGY STAR guidelines for energy efficiency.